I have a hot cupboard fed via a 13A socket. 2.9Kw load. The unit is plugged in and unplugged 2 times a day and the constant use is waring out contacts and pin covers.
I am looking to use a 16A comando socket. The circuit is 16A rcbo protected. And the cable supplying hot cupboard is rated at 16A. As the cupboard is unable to over current and the flex is good for fault current can I omit the 13A which was in the 13A plug supply?